|Open Stud Stage Rough Wiring for Receptacles, Switches, High Hats, Appliances and LAN.|
What is needed for rough in wiring inspection?
What is needed at each outlet and wall box?
Ask us anything about wires, cables, grounding codes at lights/boxes and pigtails.
Ask us what the inspector wants to see, and what is needed before drywall.
Accent Lighting: the directional to emphasize a particular object or to draw attention to a part of the field of view. Baffle a single opaque or translucent element to shield a source from direct view at certain angles, or to absorb
unwanted light. Beam Angle the angle You can save a lot of money by doing your own wiring. Here we'll show you to wire an entire room. Even if you've never picked up an electrical tool in your life, you can safely rough-in wiring by following the directions in this article.
You'll learn all of the pro techniques for a wiring job, including choosing the right size receptacle boxes, running cable throughout the room, and making the electrical connections.
|Kitchen Receptacles - Code Summary|
In the kitchen and eating areas every counter space wider than 12 inches must have a GFI protected plug, in general all kitchen counter top plugs should be GFI protected. Countertop receptacles shall be installed so that no point along the wall is more than 24" measured
horizontally from a receptacle outlet in that space. Peninsular bars and islands 12" or wider shall have at least one receptacle. Exception: Tennessee Code in dwelling unit’s section states, “The installation of receptacles for island counter spaces and peninsular counter
spaces below the countertop shall be optional.
At least two 20-ampere branch circuits are required to feed receptacle outlets for small appliance loads, including refrigeration equipment in the kitchen, pantry, breakfast room, and dining room. These circuits, whether two or more are used, shall NOT supply anything
other than receptacles in these areas. Lighting outlets and built-in appliances such as garbage disposals, hood fans, dishwashers, and trash compactors are NOT permitted on these circuits. Kitchen counter top receptacles must be supplied by at least two small appliance branch circuits.
Kitchen appliance and convenience receptacles must be on 20 amp breakers, and wired with 12 gauge wire.
Required Ground Fault Protection. A ground fault circuit interrupter must protect ALL receptacles listed below:
Bathroom receptacles, Outdoor receptacles, Garage receptacles.
Kitchen receptacles that serve counter top surfaces.
Counter top receptacles within 6 feet of a wet bar sink.
All receptacles in an unfinished basement:
Sump pumps, Crawl spaces at or below grade.
Spas, Hydro massage, Hot tubs and associated electrical components.
Pretty much any location where water and electricity might mix.
Required Arc Fault Circuit Interuptor protection - 208 NEC 210.12 (A)" An arc fault circuit interuper - AFCI is a device (usually if not always a breaker) designed to give protection from arc faults. An AFCI breaker will trip whenver an arc is detected. In all dwellings an arc
fault circuit interrupter must protect ALL 120 volt 15 and 20 amp single phase receptacles in family rooms, living rooms, parlors, recreation rooms, dining rooms, libraries, dens, sunrooms, recreation rooms, closets, hallway or similar rooms. In other words pretty much all
receptacles inside of a dwelling except the bathrooms, kitchen, laundry and garage must be AFCI protected.
Appliance Branch Circuits - Code Summary
The following Appliances must be on a separate 20-amp circuit: Dishwasher, Garbage disposal, Washing machine. As a general rule All 240-volt appliances must be on their own circuit. Hot tubs, garden tubs, Jacuzzis and the like must be GFI protected and wired as required for
the particular model and local codes. The service areas of all appliances must be accessible after the final finish is complete.
Required Light Fixtures - Code Summary
General Lighting Branch Circuits shall be computed on a three watts per square foot basis. You may wire up to 600 square feet of living area on a 15 ampere branch circuit or up to 800 square feet on a 20-ampere circuit. These branch circuits may supply lighting outlets in all
areas of the dwelling and convenience receptacles, other than Small Appliances, Laundry, Bathroom, or HVAC - as outlined above. Every room, hallway, stair way, attached garage, and outdoor entrance must have at least one light fixture controlled by a wall switch. However,
in most rooms other than kitchens and bathrooms, the wall switch may control one or more plugs into which lamps may be plugged instead of a ceiling or wall mounted fixture. There must be at least one wall switch controlled light in a utility room, attic, basement or under
floor space used for storage or which contains equipment such as heat and air, water heaters, sump pumps, etc. which may ever require service. The switch must be located at the entry point to these areas. Hallways and stairs with more than six steps require the lights to
be controlled by a switch at each end. In closets, fluorescent fixtures must have at least 6 inches of clearance away from shelves or storables. In a typical two foot deep (approx.) closet, the fixture will be mounted on the wall just over the door. In summary, put a
light in every room or large closet, outside of every exterior door, and under the floor and in the attic if there is electrical equipment in these spaces or if they are suitable for storage. Switch the room lights at every door entering the room, switch a hall or stairway
at both ends, and switch exterior lights at the doors which they service. As a rule of thumb you can put up to ten average light fixtures on a single circuit, unless this will add up to excessive wattage for the circuit (note, a ceiling fan and light kit qualify as one fixture).
Notable exceptions would be floodlights, which are high wattage fixtures. Four double bulb floodlights would pretty well fill up a circuit by themselves. The actual rule for this is to not exceed 80% of the calculated wattage capacity of the circuit. Wattage capacity of the
circuit equals the amp rating of the breaker times the voltage (120), so for a typical 15 amp light circuit add up all of the maximum wattage's and make sure that they are less than 80% of 15x120 (1440 watts max). Keep in mind that the inspectors may be looking for no more
than 10 fixtures (more or less according to local variances) per circuit.
Newtown Square PA - Electrical Workers Lending a Hand for the small jobs around the house.
The Electrician to The Main Line, every electrical problem solved.
The Electrician - Springfield, PA 19064, wiring for receptacles and lighting fixtures.
Electrician - Havertown, PA 19083 for Home, Business or Multi-Tenant Property.